There are special inspectors for certain aspects, but, on this particular SFR the first inspection is what you see to verify the rebar. Next the contractor covers the holes with plywood and after the pour the next inspection verifies that the concrete made it all the way down along with a hammer test verifying the webs are solid wherever they are required to be.I thought you had special inspectors who are supposed to be on site when things like that happen. To verify it was actually done.
I usually just see 1" holes in the bottom course and watch some grout squirt out. I check the rebar when the wall is being constructed. I only ever looked at tall commercial fire walls