The short conductors have not been explained. I am still waiting to hear what Edison has to say.What was proposed to take care of the undersized and too short conductors? With the parallel conductors used by panel manufacturers between the load side of the meter & the main breaker, in the 3rd photo from the bottom the PoCo UG feed seems to be the only place the that CT's could be placed, still wrong IMO. What does SCE do about if when they find out about it?
R311.5.1 Attachment. Exterior landings, decks, balconies,
I disagree. It looks like 2x12 dimensional lumber, might be spf rather than syp. No hangers ... agree with that. But it looks like the top end of the stringers are high enough that they would be bearing on the floor joist if the advantech was not there. The middle stringer appears yo have a full size advantech doubler, and all have a 2x4 doubler on the bottom edge.- the top of the stringers are bearing only on the 3/4" piece of plywood,
Yeah, if they had more of the stringer against the joist I probably wouldn't have worried. They got an engineer, who had them add some hangers and some brackets and called it good. Works for me...I've seen it done that way with a piece of 3/4-inch sheeting but in my case more of the stringer is against the double floor joist.